A process area alarm activated. The alarm was caused by an instrument channel located above a reaction vessel off-gas system final HEPA filter canister, which indicated 25% of the lower explosive limit (LEL) for hydrogen. Since the only source of hydrogen is from the reaction vessel during the reaction of sodium with concentrated sodium hydroxide, the immediate actions were to shutdown the reaction process and place the facility in a safe condition.
The root cause was inadequate or defective design. Had the pre-filter drains been vented to outside the building, no hydrogen could accumulate in the process area. The corrective action for this is to complete an Engineering Task Authorization (ETA) to install a sample/drain collection system with loop seals to prevent any release of view more