A hydrogen leak occurred from a 1-inch gate valve on a makeup gas line in an oil refinery gas oil hydrotreater unit. When the leak was discovered, the gas oil hydrotreater unit shutdown procedures were immediately implemented and emergency response was requested. The refinery response team along with county response teams responded, and after approximately 1/2 hour, the gas oil hydrotreater unit was fully shut down. Shutdown consisted of sufficiently depressurizing the unit and adding nitrogen to allow safe closing of the leaking 1-inch gate valve and installation of the associated missing bull plug.
During this event, the 1-inch gate valve was found to be open roughly 10% with no bull plug in the valve, allowing the hydrogen to leak to the atmosphere. In addition, a 1-inch bull view more