During a facility walk-through, it was noted that a combustible gas (hydrogen) monitoring system installed in a furnace room was inoperable (the system had been unplugged). This system is used to detect and warn facility employees of an explosive or flammable environment. An explosive or flammable environment can only occur if there is a leak in the system, which would not be expected to occur during normal operations. When the system was reactivated, no leaks were indicated.
The incident had the following three causes:
A procedure describing administrative controls necessary to ensure safe operations in the area should have been developed and implemented prior to disabling the hydrogen monitoring system.
The hydrogen monitor was not hard-wired, which allowed it view more