A metal hydride storage system was refilled using compressed hydrogen in a closed lab environment. The tank system is an in-house development and is optimized for high hydrogen storage density and use with an air-cooled fuel cell. The system is equipped with a pressure relief valve that opens gradually at 35 bar to protect the tank from overpressure conditions. The tank itself is designed to adsorb 400 g of hydrogen at a pressure less than 15 bar.
For refueling, the secondary pressure on the compressed hydrogen supply container was set to 20 bar and the adsorption of the hydride was started without hydrogen flow limitation. Due to the exothermic nature of the hydride upon recharge, as expected a sharp increase in tank temperature was measured. The tank was uncooled because the view more