An explosion at a coal-fired power plant killed one person and injured 10 others. The blast killed the delivery truck driver who was unloading compressed hydrogen gas, which is used to cool the plant's steam generators. Hydrogen deliveries are routine at the plant, occurring about once a week. Evidence pointed to the premature failure of a pressure-relief device (PRD) rupture disk, which had been repaired by the vendor six months prior to the explosion.
A hydrogen explosion occurred at a plant, damaging a wall adjacent to the hydrogen storage assembly. The investigation revealed that the explosion was the consequence of deficiencies in components integral to the hydrogen storage assembly, and that this assembly belonged to a supplier contracted to provide hydrogen to the plant. The analysis revealed that had the supplier properly installed and maintained this equipment, this incident would have been prevented. By receiving assurance, on an ongoing basis, that the supplier was properly maintaining this equipment, the company could have also reduced the chance of occurrence of this incident.
A hydrogen supplier was awarded a contract in 1990 to supply the plant with hydrogen as well as to provide view more
A pressure relief device (frangible burst disk) on one of a hydrogen delivery tube trailer's 26 tubes failed prematurely and released hydrogen while filling a hydrogen storage tank at a government facility (see Attachment 1). Prior to the filling process, all procedures and safety checks, including connection to the facility's regulator/distribution control system with leak checking and follow-up verification of leak checking by facility personnel, were completed (see Attachment 2 for more details). During the filling process, a person walking near the facility heard the noise of escaping gas that included occasional popping sounds typical of bursts of gas release. Facility personnel were alerted and the tube trailer vendor's incident response team was dispatched to the view more