A deficiency was discovered in the application of a hydrogen sensor in the Rotary Mode Core Sampling (RMCS) portable exhauster. The sensor is installed in the flow stream of the exhauster designed to be used with a RMCS truck for core sampling of watch list tanks, and is part of the flammable gas detector system. During the previous week, a quarterly calibration of the sensor, per maintenance procedure, was attempted by Characterization Project Operations (CPO) technicians. Ambient temperatures during the sensor calibration were approximately 20 to 30 degrees F. Inconsistencies in calibration results and the failure of the sensor to meet the response-time calibration requirement lead to the conclusion that the unit could not reliably perform its safety function at low ambient view more
A hydrogen gas detector on the ground floor of a building registered the release of a small amount of hydrogen gas and actuated automatic alarms both at the fire department and in one of its buildings. Additionally, interlocks connected to the gas detector completely shut down the experiment. Upon hearing the alarm, all occupants (about 6) promptly left the building. Fire department personnel are housed in the trailer next to a building and responded within one minute. They tested the atmosphere within the building, reset the gas detector, and secured the alarm at 9:15. The alarm was actuated when an experimenter assigned to the experiment was evacuating lines using a vacuum pump.
The speed of evacuation was controlled by a commercially manufactured flow meter. It is believed view more