A person working in a hydrogen lab unknowingly closed the wrong hydrogen valve and proceeded to loosen a fitting in one of the hydrogen gas lines. The pressure in the 1/4"-diameter hydrogen line was approximately 110 psig. Hydrogen escaped from the loosened fitting and the pressure release resulted in the tubing completely detaching and falling to the floor. The person noted seeing a white stream around the hydrogen jet leak. The person noted a color change and noise change as the leak ignited (this happened in a matter seconds and he did not have a chance to react). The person left the lab and pushed the emergency stop button. Someone else pulled the fire alarm. Both of these actions were designed to close the main hydrogen solenoid (shutoff) valve. The local emergency response view more
One man was killed and another severely injured while working with a portable battery power supply.
At a test facility, a water-submersible portable battery power supply was used to power lighting. The battery power supply contained two 12-volt lead-acid automotive batteries, a wiring harness, and switching relays mounted in an air-tight case suitable for submersion in water. The case possessed ½-inch aluminum walls and a 13.8-pound lid. The box had been used periodically over two years.
After charging all night, the battery power supply was moved into place and connected to the lighting. Two technicians started to test the unit. One technician rested his hand on the case lid while the second leaned over the lid and threw the switch to activate view more