While research staff were working in a lab, a staff member opened the primary valve to a 0.2" (1500 psi) hydrogen gas line connected to a manifold supplying instruments in the lab. Upon opening the valve, the hydrogen gas line failed at a fitting on the switching manifold, releasing a small amount of hydrogen gas. The staff member closed the valve immediately, then inspected the gas line and found the front ferrule (of the compression-style fitting) to be missing. There were no injuries or damage to equipment.
In the follow-on discussion with research staff, it was learned that approximately one month earlier, a similar condition (front ferrule missing from a fitting) was found while performing a modification to a similar manifold. Following a critique, management expressed view more