A significant hydrogen leak occurred during refueling of the onboard hydrogen storage tank of a fuel cell-powered lift truck while it was completely depowered. The in-tank shutoff solenoid valve had recently been replaced, and this was the initial refueling event after the replacement. The fuel zone access panel was removed to allow constant visual leak checking with Snoop leak-detection fluid. The event occurred during the final pressure testing of the repaired system when an O-ring failed at approximately 4500 psi, releasing the entire contents of the hydrogen tank in about 10 minutes. The dispenser hose/nozzle was immediately disconnected, and the leak location was quickly isolated to the tank/valve interface. A 30-foot boundary around the lift truck was cleared of personnel and view more
During maintenance on a breakaway fitting, a review of the pressure rating of the adapter fitting connecting the pipe to the breakaway found the adapter to be under rated for the design pressure. While the male straight-thread side of the "standard" fitting was rated to 7700 psig, the female compression-tube end of the same fitting was rated to only 4900 psig. The adapter was replaced with a fitting of increased wall thickness meeting the design pressure rating.
A hose clamp failed on a low-pressure vent line from a hydrogen reactor experiment and effluent was leaked into the laboratory. Unburnt hydrogen in the effluent stream triggered the low-level hydrogen alarm. The hose clamp was resecured and other hose clamps were checked for proper tightness.
During operation of a succinic acid plant, hydrogen leaked from a mounting joint on a safety valve at the upper part of a reactor, which generated a hydrogen flame. Prior to the incident, the safety valve was removed and reattached during an inspection at a turnaround shutdown. An incorrectly sized, smaller gasket was installed on the joint, and the tightening force on the bolts was inadequate. Therefore, a gap was generated as time went by and un-reacted hydrogen leaked.
In the case of many leak tests after construction, a leak is checked by a soap test after pressurizing piping and facilities for the test. (A soap test is conducted by pouring soap suds at the place to be checked (mainly a joint part) after pressurizing. If bubbles are found, view more
A laboratory research technician entered a lab to begin preparing samples that were to ultimately be purged in an anaerobic chamber (glove box) located in that room. As the technician walked into the lab, she looked at the chamber to see if it was adequately inflated. This chamber is equipped with a gas concentration meter, capable of simultaneously displaying the oxygen and hydrogen concentrations of the chamber atmosphere. Under normal operating conditions, the atmosphere inside the chamber is comprised of 0% oxygen (as intended/desired for an anaerobic atmosphere), approximately 2-3% hydrogen, and with the remaining balance being nitrogen (approximately 98-97%). Under such normal operating conditions, the hydrogen concentration inside the chamber is less than the lower explosive view more
An individual inadvertently connected a pure hydrogen gas bottle to a chamber/glove box as opposed to a 10% hydrogen (in nitrogen) bottle that should have been used. [The wrong bottle had mistakenly been delivered, and the inexperienced individual did not know the difference.] The hydrogen concentration increased within the chamber to about 9%. Since there was insufficient oxygen in the chamber to support combustion, the hydrogen did not burn, and was quickly diluted with nitrogen.