A distillate dewaxing unit at an oil refinery was undergoing hot hydrogen regeneration of the catalyst when an explosion occurred. Catalyst regeneration is a periodically performed procedure, in which the normal liquid hydrocarbon feed is stopped and a hydrogen-rich gas mixture is fed through the catalyst bed for which the normal operating temperature is raised from 700F to 800F. During the catalyst regeneration process the reactor pressure is increased from normal operating levels just below 600 psig to about 640 psig. A pipe failure occurred as a sudden and complete rupture of the 10-inch diameter line at the exit of one of the two reactors. Security video revealed that the release rapidly exapnded and the hot gas mixture ignited shortly after rupture. A shock wave from the resulting view more
A hydrogen leak at the flange of a 6-inch synthesis turbocharger valve in an ammonia production plant ignited and exploded. Hydrogen detectors and the fire alarm alerted the control room, which immediately shut down the plant, and the fire was then extinguished rapidly. There were no injuries caused by the accident, since the operator heard a wheezing sound and was able to run away just before the explosion occurred. The leaking gas was composed of 70% hydrogen at a flow rate of 15,000 cubic meters per hour. Property damages in the turbocharger included electrical cabling, melted siding, and heavily damaged pipes. The ammonia plant was shut down for more than a month.Five days before the incident, a problem with the CO2 absorber column led operators to open the vent downstream of the view more
A steel tube with inner diameter of 6 mm and 10 m length was filled with radiolysis gas (stoichiometric H2-O2 mixture) at 70 bar for boiling water reactor simulations. Via a pneumatic valve, a venting line with similar cross-section and 2 m length, filled with atmospheric air, was connected.
For venting the tube, the valve was opened (fast) and an explosion occurred.
Explanation: Due to diffusion ignition in the leading shock, a flame flashed back into the pre-mixed reservoir and induced a detonation there. The tube system and involved measurement technique was destroyed. For safety reasons, the whole installation was set up in a protective container so that no person or other equipment was threatened.