Two scientists were changing hydrogen gas cylinders in an analytical laboratory. They were in the process of removing the cylinder cap from the new cylinder when a loud hissing noise occurred and they quickly realized that the tank was leaking. After making a quick attempt to shut off the tank, which was not possible, they left the lab and notified their supervisor.
After checking that everyone was out of the lab, the supervisor paged all staff in the vicinity to immediately evacuate to the staging area. Facility management and ES&H management were notified about the situation, and they contacted the local fire department to respond to the site in case the venting gas was ignited.
The first responders arrived quickly and spoke with facility management and the site view more