A person working in a hydrogen lab unknowingly closed the wrong hydrogen valve and proceeded to loosen a fitting in one of the hydrogen gas lines. The pressure in the 1/4"-diameter hydrogen line was approximately 110 psig. Hydrogen escaped from the loosened fitting and the pressure release resulted in the tubing completely detaching and falling to the floor. The person noted seeing a white stream around the hydrogen jet leak. The person noted a color change and noise change as the leak ignited (this happened in a matter seconds and he did not have a chance to react). The person left the lab and pushed the emergency stop button. Someone else pulled the fire alarm. Both of these actions were designed to close the main hydrogen solenoid (shutoff) valve. The local emergency response view more
A researcher was working with hydrogen storage materials in a laboratory. Several other researchers were working in adjacent laboratories.
The researcher had prepared a sample of aluminum deuteride, AlD3, by reacting lithium aluminum deuteride and aluminum chloride in diethyl ether. The actual composition/phase of the material synthesized was unknown, but the researcher had attempted to produce the gamma phase of aluminum deuteride. The synthesis steps used to produce the material were complete and the researcher attempted to seal the material in a glass ampoule for offsite shipment and analysis. The sample size was approximately 1 gram.
The ampoule with the sample had previously been placed under vacuum and had been isolated from the atmosphere. The process for sealing view more