An explosion occurred at a chemical plant in an analysis room containing various analyzer instruments, including a gas chromatograph supplied with hydrogen. A contract operator was performing work to install a new vent line to a benzene analyzer that was part of a group of CO2 analyzers, but separate and unrelated to the gas chromatograph. During the process of this work, a plant supervisor accompanying the contract operator doing the work had an indication of flammable gas present on a portable detector. This was in conflict with the fixed gas detector in the analysis room that was indicating that no flammable gas was present. As a precaution, the plant supervisor immediately cut off the hydrogen supply and, along with the contract operator, began the normal task of determining if view more
Within the International Space Station (ISS) oxygen generator, an increase in differential pressure across a pump supplying return water to a PEM electrolyzer fuel cell stack had persisted over a 4-month period and was approaching the shut-off limit for the system. This decrease in performance was suspected to be caused by water-borne catalyst fines containing platinum black and Teflon®* binder materials, shed by the fuel cell stack, and accumulated within the pump's inlet filter. Maintenance in the field was required.
The system had been designed for factory maintenance, and no contingency had been planned to handle field maintenance for such a circumstance. An initial assessment of hazards for the proposed filter maintenance raised the concern that opening the water line view more
A water treatment plant used an electrolytic process to generate sodium hypochlorite (NaOCl) from sodium chloride (NaCl). The strategy of using liquid sodium hypochlorite for disinfecting water instead of gaseous chlorine (CL2) is popular because the liquid is generally safer and falls under fewer OSHA and EPA standards. The further idea of generating the liquid sodium hypochlorite on an as-needed basis and in limited quantities also has certain obvious safety advantages.
One of the disadvantages of the electrolytic process is that hydrogen gas is also created as a byproduct. The hydrogen is supposed to be vented, by design, to the atmosphere before the liquid sodium hypochlorite passes into a holding tank.
For various reasons, in this instance it is believed that the view more