An explosion occurred at a chemical plant in an analysis room containing various analyzer instruments, including a gas chromatograph supplied with hydrogen. A contract operator was performing work to install a new vent line to a benzene analyzer that was part of a group of CO2 analyzers, but separate and unrelated to the gas chromatograph. During the process of this work, a plant supervisor accompanying the contract operator doing the work had an indication of flammable gas present on a portable detector. This was in conflict with the fixed gas detector in the analysis room that was indicating that no flammable gas was present. As a precaution, the plant supervisor immediately cut off the hydrogen supply and, along with the contract operator, began the normal task of determining if view more
An instrument engineer at a hydrogen production facility was arresting the hydrogen leakage in tapping a pressure transmitter containing 131-bar hydrogen gas. The isolation valve was closed and the fittings near the pressure transmitter were loosened. The pressure dropped from 131 bar to 51 bar. The fitting was further loosened (though very little); the instrument tube slipped out of the ferrule and got pulled out of the fitting. With the sudden release of the 51-bar hydrogen, there was a loud pop (like a fire cracker) and the spark-proof tool was observed to have black spot on it. The volume of the hydrogen gas released was small, since it was in the tapping line only.