During restart of an ammonia production plant, syngas (50% hydrogen mixed with methane, ammonia, and nitrogen) leaking from a flange directly downstream of the synthesis reactor ignited. The plant had been shut down for about 90 minutes due to a technical problem. Alerted by the plant fire alarm, the operator activated the emergency shutdown, which isolated and depressurized the synthesis loop. Steam was sprayed onto the leak site to dampen the fire, which was brought under control 55 minutes later. Property damages included pipe insulation, the reactor's protective shutters, concrete fireproofing of the reactor structure, and instrumentation cables within 3 meters of the leak site. The flames did not affect the synthesis reactor itself, which was protected by a deflector. The view more
Hydrogen was released near the ground when the vent line from a 13,000-gallon liquid hydrogen storage vessel suffered damage from unusually high winds. The toppled vent line did not shear or tear, but sustained a kink that restricted hydrogen flow and created a back pressure on the vessel relief system.
Repair efforts were hampered by the potential for cold hydrogen gas, a flammability hazard, in the work area. Shut off or redirection of the hydrogen was not possible, and variable breezes made set up of safe zones uncertain. A protocol had not been prepared for this scenario.
The System Shutdown logic activated and the compressor automatically shut down on high vibration. When the operator investigated the unplanned shutdown, two broken compressor head fasteners were noted lying on the deck.
During start-up operation of a high-temperature, high-pressure plant using hydrogen, hydrogen gas leaked from the flange of a heat exchanger and a fire occurred. The leakage occurred for two reasons:
Insufficient tightening torque control was carried out during hot-bolting and an unbalanced force was generated across the bolts.
A temperature rise was induced across the heat exchanger as a result of a revamping activity, during a turnaround shutdown.
Hot-bolting: In equipment and piping that operate at high temperatures, as the temperatures rise, the tightening force decreases, thus re-tightening of bolts is necessary. This work is called hot-bolting. The design conditions of the evaporator where the fire occurred were 2.4 MPaG, view more