A hydrogen alarm sounded when hydrogen buildup occurred in an unmanned switching room containing backup lead acid batteries after the exhaust ventilation fans failed to start at the 1% hydrogen trigger level. Failure of the ventilation fans to vent the normal off-gassing hydrogen from the lead acid batteries resulted in the hydrogen concentration in the room increasing to 2%, which triggered the hydrogen alarm. The alarm was automatically sent to an alarm-monitoring company that alerted the local fire department as well as company personnel of the condition. The fire department was dispatched to the scene and, along with company personnel, provided secondary ventilation to lower the hydrogen concentration to normal conditions. Hydrogen leakage from lead acid batteries is normal, and view more
A power plant reported a hydrogen leak inside an auxiliary building. The given plant was in cold shutdown at the time of the event. The discovery of this problem was as a result of an unassociated event involving the activation of a chlorine monitor in the control building. When additional samples indicated no chlorine gas, the shift supervisor ordered further investigation into other plant areas. Because there was no installed detection equipment, portable survey instruments were used to determine gaseous mixtures. Hydrogen was detected in the auxiliary building at 20 to 30 percent of the lower flammability limit (LFL) for hydrogen. A level of about 30 percent of LFL corresponds to about 1.2 percent hydrogen by volume.
When hydrogen was discovered in the auxiliary building, the view more
A routine security patrol reported a strong odor of sulfur coming from a battery charging facility. The battery charging facility is used for charging the various forklift batteries for the shipping and receiving operation. The building is approximately 450 sq. ft. and has four charging stations. Emergency response was initiated and the incident commander responded to the scene. Initial air monitoring indicated readings above the Lower Explosive Limit (LEL) for hydrogen gas. The local fire department responded and setup for the situation. Facilities personnel responded and turned power off to the building. The building was ventilated and verified to be safe by the fire department. There were no injuries or damage.
The exhaust fan for the building failed, allowing hydrogen gas to view more