In early afternoon, a northbound tractor-semitrailer with horizontally mounted tubes filled with compressed hydrogen at approximately 2400 psi (166 bar) was struck by a northbound pickup truck that veered into the semitrailer's right rear axle. According to witnesses, the tractor-semitrailer then went out of control and left the roadway, coming to rest approximately 300 feet (91 meters) from the point of impact. As a result of rotational torque and impact, the end of one tube was sheared off at the bulkhead and left the tube bundle. During the process, some of the tubes, valves, piping, and fittings at the rear of the semitrailer were damaged and released hydrogen. The hydrogen ignited and burned the rear of the semitrailer. In the meantime, the pickup truck had also run off the view more
A hydrogen leak occurred at a plant's hydrogen fill station when a vendor's hydrogen fill truck trailer pulled away after filling and caught an improperly stored hydrogen fill line. The driver of the hydrogen truck trailer did not properly stow the hydrogen fill line after filling and failed to verify that the hydrogen fill line was clear of the trailer prior to departure. As the driver pulled away from the fill station, the hydrogen fill line caught on the trailer and subsequently pulled on the hydrogen fill station's ground storage tubes distribution manifold. The force of this pull bent the plant's hydrogen distribution manifold and hydrogen began leaking from a threaded connection and from the hydrogen fill line. The truck trailer driver reported hearing a view more
A pressure relief device (PRD) valve failed on a high-pressure storage tube at a hydrogen fueling station, causing the release of approximately 300 kilograms of hydrogen gas. The gas ignited at the exit of the vent pipe and burned for 2-1/2 hours until technicians were permitted by the local fire department to enter the station and stop the flow of gas. During this incident the fire department evacuated nearby businesses and an elementary school, closed adjacent streets, and ordered a high school to shelter in place.
There were no injuries and very little property damage. The corrugated roof on an adjacent canopy over a fueling dispenser was slightly singed by the escaping hydrogen flame, causing less than $300 in damage.
The station's operating systems worked as view more