An explosion at a coal-fired power plant killed one person and injured 10 others. The blast killed the delivery truck driver who was unloading compressed hydrogen gas, which is used to cool the plant's steam generators. Hydrogen deliveries are routine at the plant, occurring about once a week. Evidence pointed to the premature failure of a pressure-relief device (PRD) rupture disk, which had been repaired by the vendor six months prior to the explosion.
One man was killed and another severely injured while working with a portable battery power supply.
At a test facility, a water-submersible portable battery power supply was used to power lighting. The battery power supply contained two 12-volt lead-acid automotive batteries, a wiring harness, and switching relays mounted in an air-tight case suitable for submersion in water. The case possessed ½-inch aluminum walls and a 13.8-pound lid. The box had been used periodically over two years.
After charging all night, the battery power supply was moved into place and connected to the lighting. Two technicians started to test the unit. One technician rested his hand on the case lid while the second leaned over the lid and threw the switch to activate view more
In early afternoon, a northbound tractor-semitrailer with horizontally mounted tubes filled with compressed hydrogen at approximately 2400 psi (166 bar) was struck by a northbound pickup truck that veered into the semitrailer's right rear axle. According to witnesses, the tractor-semitrailer then went out of control and left the roadway, coming to rest approximately 300 feet (91 meters) from the point of impact. As a result of rotational torque and impact, the end of one tube was sheared off at the bulkhead and left the tube bundle. During the process, some of the tubes, valves, piping, and fittings at the rear of the semitrailer were damaged and released hydrogen. The hydrogen ignited and burned the rear of the semitrailer. In the meantime, the pickup truck had also run off the view more
Forty-six hydrogen cylinders were accidentally charged with air instead of additional hydrogen during recharging operations at a synthetic liquid fuels laboratory. Cylinders were manifolded in batches of 10 or 12 to the utility compressor outside the laboratory. In normal operations, partly used cylinders containing hydrogen at a pressure of 800-900 psi were recharged to a pressure of 2000-2100 psi. Since the contaminated cylinders contained a highly explosive mixture of about 40% hydrogen and 60% air, it was decided to release the compressed gas to the atmosphere outside the building after grounding the cylinders. Two of the cylinders were successfully discharged, but an explosion occurred while the third cylinder was being discharged. Two chemical engineers were killed by the blast, view more
Operators in a powdered metals production facility heard a hissing noise near one of the plant furnaces and determined that it was a gas leak in the trench below the furnaces. The trench carried hydrogen, nitrogen, and cooling water runoff pipes as well as a vent pipe for the furnaces.
Maintenance personnel presumed that the leak was nonflammable nitrogen because there had recently been a nitrogen piping leak elsewhere in the plant. Using the plant's overhead crane, they removed some of the heavy trench covers. They determined that the leak was in an area that the crane could not reach, so they brought in a forklift with a chain to remove the trench covers in that area.
Eyewitnesses stated that as the first trench cover was wrenched from its position by the forklift view more
An explosion occurred in a 90-ton-per-day incinerator at a municipal refuse incineration facility. Three workers were seriously burned by high-temperature gas that spouted from the inspection door, and one of them died 10 days later. The accident happened during inspection and repair of the furnace ash chute damper. The workers injected water to remove some blockage, and the water reacted with incinerated aluminum ash to form hydrogen, which caused the explosion.
Workers noticed that the post-combustion zone was full of ash and the ash pusher was not working properly, so they tried to remove the ash from the inspection door with a shovel. They discovered a solid layer of "clinker", which is formed by solidification of molten material such as aluminum. The explosion view more
A hydrogen explosion and fire occurred in the benzene unit of a styrene plant in a large petrochemical complex. The unit was being restarted following a scheduled maintenance shutdown. The explosion followed the release of about 30 kilograms of 700-psig hydrogen gas from a burst flange into a compressor shed. Two men were killed and two others were injured. If it had not been a holiday, the death toll and injuries would probably have been much worse.
The operators were bringing the plant online and increasing the hydrogen circulation pressure. About 10-15 seconds before the explosion, they heard a pop and then a loud hiss of pressure being released within the compressor shed. Witnesses reported seeing a white flash and then a large fireball. The fires burned out in 2-3 minutes, view more